時間：2018-06-25 17:27 作者：admin 返回列表
In recent years, haze, ozone pollution and acid rain that affect people's lives are closely related to nitrogen oxides (NOx). Nitrogen oxides (NOx) have great damage to the environment. The combination of nitrogen oxides and water in the air will eventually convert into nitric acid and nitrate. Nitric acid is one of the reasons for acid rain; it can produce photochemical smog under certain conditions.
With the development of large capacity and high parameters in the direction of boiler units, it is the goal of modern combustion technology to achieve high efficiency combustion, reduce pollutant emission, improve the adaptability of coal and improve the safety and reliability of operation. Among them, the effective reduction of NOx emissions is the first place.
1. NOx 排放
為了達到充分燃燒的極限過剩空氣係數為大約1.1, 對應的理論尾氧含量為大約2%. 更高的尾氧含量通常意味著燃燒器效率的降低。理想的燃燒器最好尾氧含量可以控製在3%以內；市場上表麵燃燒的燃燒器的尾氧含量通常在7%左右，相對於3%的尾氧含量，意味著產生相同的熱量，需要多耗費大約6~8%的天然氣。對於常年運轉或者設備長期在較高負荷運轉，天然氣消耗量比較大的業主，選擇一款尾氧含量低的燃燒器對於降低運行成本至關重要。
Main parameters of low nitrogen burner selection
1. NOx emission
It is necessary to meet the national and local environmental emission requirements. On the premise of meeting the requirements, from the point of view of the social responsibility of the enterprise, we should choose the lower NOx emission equipment as far as possible.
2. tail oxygen content
To achieve full combustion limit excess air coefficient is about 1.1, the corresponding theoretical tail oxygen content is about 2%. higher tail oxygen content usually means reducing the burner efficiency. The best tail oxygen content of the ideal burner can be controlled within 3%; the tail oxygen content of the combustor on the market is usually about 7%, compared with the 3% tail oxygen content, which means that the same amount of heat is produced and the natural gas of about 6~8% is needed. For the owners who run for a long time or the equipment is running at a high load for a long time and the gas consumption is large, it is very important to choose a burner with low tail oxygen content to reduce the operating cost.
3. adjustable ratio
The low nitrogen burner with electronic proportional adjustment should normally have a high adjustable ratio of at least 5:1. The lower adjustable ratio means more ON/Off startup and shutdown in actual operation, and at the same time it means more natural gas consumption. It is very important to choose a high adjustable burner for reducing the consumption of natural gas, reducing the operating cost and prolonging the service life of the equipment, unless it is a boiler in a relatively small stable interval.
4. other major considerations
Combustion stability is the main consideration for choosing low nitrogen burner, including the reliability of the equipment itself. Before the implementation of the low nitrogen standard in Beijing, the world wide range of low nitrogen standards is mainly in the United States, so basically only the major sales markets in the United States have a long experience in the field of low nitrogen burner in the field of burner.